CCC-P01-H1 outdoor cable transfer box
CCC-P01-H1 outdoor cable transfer box features:
1. Dimensions: 1000 × 750 × 320 (mm) (height × width × depth) (without the base)
Base size: 370 × 750 × 320 (mm) (height × width × depth)
2. Outdoor landing base installation method
3. Domestic double-layer stainless steel box, labyrinth seal structure, IP65 with protection grade GB4208-1993, beautiful appearance, long service life, can withstand the adverse effects of various outdoor climates and environments
4. The overall sealing performance of the equipment is good. The box wall and the box door are double-layered sandwich structure, and the interlayer is filled with polyurethane foam material, which has excellent heat insulation performance. The top of the box adopts a special convection channel structure and is sandwiched with sponge. The internal pressure of the box is used to prevent moisture condensation caused by drastic changes in the temperature inside the box, effectively preventing corrosion of internal equipment and effectively preventing dust.
5. Front and rear door opening structure, full front operation
6. The structure is convenient for straight-through and simple adjustment of wiring capacity. The standard configuration wiring capacity is 288 cores, the direct melting capacity is 144 cores (non-belt) or 288 cores (bands), and the wiring part adopts 12-core fusion-fit integrated module. :FRP-P02-12; direct fusion unit with welding plate: FR-P07-12
7. Provide 4 fixed trunk cables (including cable stripping protection box) and 30 distribution cables
8. Provide strip cable protection and stripping protection box, and the optical cable after stripping is protected by plastic tube and fixed into the fuser device.
9. The bottom plate cable is introduced with a tower-type sealing sleeve structure. It is easy and quick to clamp various cables of different diameters. The periphery of the hole is coated with special sealing glue and sealed. After the introduction, the cable is fixed by double-point fixing. The rear cable armor layer and the reinforcing core are connected to the high voltage protective grounding device
10. Provide storage jumper unit, reeling disk to store excess jumper
11. The internal hardware components are made of stainless steel.
12. Reliable high voltage protective grounding device
13. Complete and clear grounding, wiring, welding identification and routing instructions
14. Product performance indicators meet the requirements of the Technical Specifications for Cable Transfer Boxes.
Corresponding parameter set not found, please add it in property template of background
FRP-P02-12 fusion matching integrated module